Can you have an inside storage room for flammable and combustible liquids that is greater than 500 square feet? Of course with an adequate fire suppression system, explosion-proof fixtures and required air exchange? According to the chart in NFPA 30, the maximum shows 500 square feet... This is a commercial printing operation... Thanks.